Guidelines for drinking water transport in the Northern Territory
Northern Territory. Department of Health
E-Publications; E-Books; PublicationNT
The purpose of these guidelines is to specify public health requirements for water carters delivering drinking water to domestic and commercial customers in the Northern Territory.; Made available via the Publications (Legal Deposit) Act 2004 (NT).
The Department of Health acknowledges and thanks the Environmental Health Branch of the NSW Department of Health and the Department of Health, Victoria. This publication is based on the NSW Health Guidelines for Water Carters (27 January 2005) and the Guidelines for Potable (Drinking) Water Transport in Victoria.; Made available via the Publications (Legal Deposit) Act 2004 (NT).
Introduction -- Legal obligations -- Water quality - Australian drinking water guidelines - Treatment -- Water tank and vehicle - Transport of drinking water - Water transport vehicle construction -- Cleaning -- Record keeping - Delivery record
Drinking water -- Standards -- Northern Territory; Drinking water -- Health aspects -- Northern Territory; Water quality management -- Northern Territory; Water supply -- Northern Territory -- Management
Northern Territory Government
10 pages ; 30 cm.
Attribution International 4.0 (CC BY 4.0)
Northern Territory Government
DEPARTMENT OF HEALTH 5. CLEANING As required under the NT Food Act 2004, all water carter equipment must be maintained in a clean and sanitary condition. This equipment includes the lining of the tank, openings, lids, seals, hoses, fitting and pipes. The cleaning process involves the removal of dirt, followed by sanitising to reduce the number of disease-causing microorganisms. The water tank/container must be cleaned and sanitised regularly. Containers and equipment that have not been used for some time will need to be cleaned and sanitised prior to use. Water tanks not being used should be drained air-dried and the inspection hatch left partly open until use. Tanks should be cleaned at a minimum every three months, by: 1. Physically cleaning the tank/container with detergent and flushing with clean water. 2. Sanitising by, (a) spraying the surfaces with a solution containing 10 mg/L free available chlorine, leaving it for 5 minutes and than rinsing off with drinking water, or (b) filling the tank with a solution containing 5 mg/L of free available chlorine, leaving for at least 30 minutes before draining and rinsing the tank with drinking water. Pipes, fitting, hoses and similar should be cleaned at a minimum monthly with a solution containing 5 mg/L of free chlorine, using the following steps: 1. Physically cleaning the equipment with detergent followed by flushing with clean water. 2. Sanitising pipes or hoses by filling them for at least 30 minutes with a solution containing 5 mg/L free available chlorine, and than rinsing them with clean water. 3. Sanitising fittings by soaking them in a solution containing 5 mg/L of free available chlorine for 5 minutes followed by rinsing with clean water. 4. Drain and air-dry equipment and store in a manner protecting them from contamination. Note: The water carter should ensure that the disposal of wash water does not cause a nuisance. For advice on wash water disposal contact the Department of Natural Resources, Environment, the Arts and Sport (NRETAS). Page 8 of 10 Department of Health is a Smoke Free Workplace
Aboriginal and Torres Strait Islander people are advised that this website may contain the names, voices and images of people who have died, as well as other culturally sensitive content. Please be aware that some collection items may use outdated phrases or words which reflect the attitude of the creator at the time, and are now considered offensive.
We use temporary cookies on this site to provide functionality.
You are welcome to provide further information or feedback about this item by emailing TerritoryStories@nt.gov.au