Bore completion report. Gan-gan outstation DLH-498 (27583)
E-Publications; ebooks; PublicationNT; E-Books; Report No 88/91
Made available via the Publications (Legal Deposit) Act 2004 (NT).
Report No 88/91
Check within Publication or with content Publisher.
Technical Report WRD91088 Viewed at 15:07:08 on 29/07/2010 Page 8 of 12. 5. RESULTS Bore 27583 was drilled at Gan-Gan Outstation and constructed with Class 9 PVC casing and stainless steel screens (see Composite Log - Bore 27583). ordinates 602200 - 8557300. The bore is located at AMG co An eight hour constant discharge test and a recovery test were conducted on the bores and water samples were collected (see Test Report - Bore 27583). 6. RECOMMENDATIONS It is recommended that: GANGAN the pump setting should be: 15m below ground level for a pumping rate of O. 5 Lis. 18m below ground level for a pumping rate of 1.0 Lis. 23m below ground level for a pumping rate of 1.5 Lis. corrosion resistant fittings should be considered when the bore is equipped. absorption trenches and septic tanks be located at a minimum of 100 metres from the bore.
Aboriginal and Torres Strait Islander people are advised that this website may contain the names, voices and images of people who have died, as well as other culturally sensitive content. Please be aware that some collection items may use outdated phrases or words which reflect the attitude of the creator at the time, and are now considered offensive.
We use temporary cookies on this site to provide functionality.
You are welcome to provide further information or feedback about this item by emailing TerritoryStories@nt.gov.au