Bore completion - Surprise Creek outstation DLH-218
E-Publications; ebooks; PublicationNT; E-Books; 69/89D
Made available via the Publications (Legal Deposit) Act 2004 (NT).
Check within Publication or with content Publisher.
Technical Report WRD89069 Viewed at 15:07:59 on 29/07/2010 Page 12 of 16. TEST REPORT - BORE RN. 26067 Bore IDeation: SURPRISE CREEK OUTSI'ATION Map: PUNGALINA 1:100 000 Sheet 6364 Grid reference: 735000 8130700 RECOMMENDATIONS Client/owner: CHent's reference: Purpose of supply: wmestic Pumping rate: 8.0 Ls. Pump setting: 27.0 m below ground ie'lei General recommendations 2re given on the reverse side. Tne aquifer and bore can;a!RlliJKl: sustain higher pumping rates with deep'er pump settings Gf fer short periods in favourable seascns. Further advice can be obtained from: PAVIA, water Directorate (In all correspondence reter to the bores RN number). SASCD House, DARiv""IN NT BORE DATA Finished depth: 63.9 m Standing water level 8.58 Construction detaiis: Interval (m) o - 6.3 o - 28 28 - 34 34 - 44 44 - 63.9 AQUIFER TEST Completion date: 21/10/88 Test date: 7/ll/SS m on 7/11/88 Test rates: 8. 0 Test duraiion 8 Description 203 mn ID Steel casino 152.4 TIm ID Steel casing 152. -4 nm ID Steel Casing with perforations 152. -4 mn ID Steel casing Open llble Notes: 1. Top of casing as constructed was 0.90 m above ground 2. All depths are measured from natural ground level 3. Test rates are not indicative of safe long term pumping rates. WARNING: MINIMUM INTERNAL BORE DIAMETER IS 152. -4 mm COMMENTS 1. The above recommendations are based on a constant rate test at 8 L/s for 8 hours and assume that hydrological conditions remain constant. 2. Provisions should be made when equiping the bore to allow water levels to be monitored while pump is operating. 3. For pumping rates to 5 Lis pump may be set at 16 metres. WATER QUALlTY See water laboratory report (Analysis No. 88/89/0930 WRD4020 L's hrs )