West macdonnells Living Area Bores 163.1 RN 16816,16817,16818 & 16819.
E-Publications; ebooks; PublicationNT; E-Books; 79/96A
Made available via the Publications (Legal Deposit) Act 2004 (NT).
Check within Publication or with content Publisher.
Technical Report WRA96079 Viewed at 02:02:15 on 18/02/2010 Page 10 of 45. I I I I I I I I I I I I I I I I I I I I 4. TEST PUMPING The two production boreholes, RN16817 andRN16818, each had a 25 hour constant rate test followed by recovery. Details of the test pumping are in Appendix B. Table 4 shows the recommended pump inlet setting and pumping rate. Test Reports are in Appendix C. Table 4. RNNumber RN16817 RN16818 Pump Settings and Recommended Pumping Rates for West MacDonnell Boreholes SWL Recommended Available Recommended Pump Setting Drawdown Pumping Rate (m btoc) (m btoc) (m) (LIs) 36.57 (06/03/97) 91.6 m 55.0 0.2 33.20 (17112196) 53.2m 120.0 0.5 Water analyses are in Appendix D. 5