Batchelor water supply development study 1985.
Keith Lane & Associated Pty Ltd
E-Publications; E-Books; PublicationNT; Report ; 68/1985
Made available via the Publications (Legal Deposit) Act 2004 (NT).
Dept. of Mines and Energy
Report ; 68/1985
Check within Publication or with content Publisher.
Technical Report WRD85068 Viewed at 15:07:30 on 29/07/2010 Page 12 of 58. I I I I I I I I I I I I I I I I I I I I stand-by power themselves is three hours are source or timers recommended if time to be avoided. that cannot reset delays in excess of Pump *2 allows a 15 second power interruption, whilst pumps #3 and *4 have no timers, and operate when power is available and only as they are required. Pump #5 has operated installed in 1982, however and was out of service July, 1984. trouble-free since it was i6 was plagued with problems for 10 months commencing in Pump *6 has operated trouble-free since its latest repair in April, 1985. This represents approximately 1500 hours of operation over the 6 month period since the repair. 5.4 Tank The existing reinforced concrete storage tank, constructed in conjunction with the establishment of the Town, is presently in such condition that minimal maintenance should be required to the year 2000. Leakage repairs have been made since the tank's construction and there is no evidence suggesting that leakage is now a problem. 8
Aboriginal and Torres Strait Islander people are advised that this website may contain the names, voices and images of people who have died, as well as other culturally sensitive content. Please be aware that some collection items may use outdated phrases or words which reflect the attitude of the creator at the time, and are now considered offensive.
We use temporary cookies on this site to provide functionality.
You are welcome to provide further information or feedback about this item by emailing TerritoryStories@nt.gov.au