Lucy creek excision, bore completion report dlh- rn 16283.
E-Publications; PublicationNT; E-Books; 47/93A
Made available via the Publications (Legal Deposit) Act 2004 (NT).
Check within Publication or with content Publisher.
Technical Report WRD93047 Viewed at 20:02:32 on 17/02/2010 Page 7 of 18. I ~ 1 1 I further drilling should occur east of this bo~~dary. Due to the poor water quality, drilling of the sandstones should be avoided. 5 RECOMMENDATIONS 1. ~~ 16283 should be equipped at a maximlli~ continuous rate of o .3 Lis. Due to the small yield available this figure should not be exceeded. 2. Means to monitor water levels and a water meter should be 3 . 4. 5. installed on the bore. The SWL and total depth of the bore should be noted each tLw plli~ping equipmnt is removed from the bore. A \"later sample should be spornitteo for full chemical analysis on a yearly basis. To . . . mlnlmlse risk of aquifer contamination no development should occur within 200 m of RL"\l 16283.
Aboriginal and Torres Strait Islander people are advised that this website may contain the names, voices and images of people who have died, as well as other culturally sensitive content. Please be aware that some collection items may use outdated phrases or words which reflect the attitude of the creator at the time, and are now considered offensive.
We use temporary cookies on this site to provide functionality.
You are welcome to provide further information or feedback about this item by emailing TerritoryStories@nt.gov.au