Annual Report 2014/2015 Utilities Commission
Tabled paper 1571
Tabled Papers for 12th Assembly 2012 - 2016; Tabled Papers; ParliamentNT
Made available by the Legislative Assembly of the Northern Territory under Standing Order 240. Where copyright subsists with a third party it remains with the original owner and permission may be required to reuse the material.
38 Item Audit finding Comment Power system security Responsibility for maintaining power system security. Not compliant At times, do not meet all requirements of Secure System Guidelines. Power system security Assess the availability and adequacy of contingency capacity reserves and reactive power reserves. Not compliant No formal assessment and not escalating these problems to Power and Water Networks. Power system security Procure adequate black start capacity. Compliant Power system security develop a Black System Restart Procedure. Compliant Had the audit been performed prior to the System Black incident of March 2014, it is likely that Power and Water would have been found not compliant. Power system security coordinate and direct any rotation of widespread interruption of demand. Part compliant No procedure. Power system Security- investigate and review all major power system operational incidents and to initiate action plans. Part compliant Late submission of incident reports. Lack of tracking of action plan outcomes. Had the audit been performed prior to March 2014, it is likely that Power and Water would have been found not compliant. Ensure that the Network Operator satisfactorily interacts with the Power System Controller. Compliant Power system stability handling single contingency events. Not compliant System Dynamic models in developing stage. Hence, a full range of stability studies have not been done. Maintenance of a secure system. Part compliant System does not always meet all requirements specified in the system secure guidelines. However, in a contingency event, controllers take action to minimise safety risks. Maintaining the frequency on islanded regions. Compliant Designating black start power stations. Compliant Approval of System Black Procedures. Not compliant No formal approval given. Although there were a number of not-compliant and part-compliant findings, overall the Commission found an adequate level of compliance with the system control licence. The Commission also noted that there were many areas of System Controls work requiring improvements to achieve acceptable practice, and that while each of these issues is small, the number of issues and their combined effect could impact on the security of the network through a lack of ability to respond correctly to an operational incident. Generation The generation licence held by Power and Water was transferred to Territory Generation on 1 July 2014 in relation to the urban and minor commercial power stations, following the
Aboriginal and Torres Strait Islander people are advised that this website may contain the names, voices and images of people who have died, as well as other culturally sensitive content. Please be aware that some collection items may use outdated phrases or words which reflect the attitude of the creator at the time, and are now considered offensive.
We use temporary cookies on this site to provide functionality.
You are welcome to provide further information or feedback about this item by emailing TerritoryStories@nt.gov.au